Wondered if any one could help me. I need an installation/engineers manual for a Minerva Marine T1008 Fire Panel.
We have just taken over the maintenance of a nursing home and need to adapt the doorlocking system to tie in with the fire alarm panel.
Any help would be appreciated ,
Thanks for the quick replies,user manual very informative, and have been in contact with Tyco who emailed me an installation manual.
We have been asked to interface the door entry system , 12 volts, to the fire alarm panel, 24 volts, so that when a full alarm situation occurs all the door locks open. Have done it numerous times with standard panels but not worked with a Minerva Marine panel before.
yeah so you take the 12v from the door system through normally closed and common contact on fire panel, then when fire panel goes, contact changes opening doors. the panel is standard its a conventioanl fire panel. if you look at the pcb when you open it the panel there will be two sets up relay contacts
most systems if its s network door entry it just needs short or a open voltage free, over the fire contact on the door entry panel, fire relay goes shorts or opens the link and all the doors release.
you can't run the door entry system off the fire alarm sounder outputs if thats what you mean by the 24v. its not allowed.
contractor999 Wrote:Thanks for all the replies.
I now have the Minerva Marine T1008 Installation Manual, and would be happy to email it to anyone who keeps this sort of info en mass.
just let me know where to send it.
Any chance of a copy please? we look after a few of these but I only have a well worn paper copy.